سال انتشار: ۱۳۸۴
محل انتشار: بیستمین کنفرانس بین المللی برق
تعداد صفحات: ۶
Pahlavanpour – Nynas Naphthenics Ltd, Wallis House, 76North Street Guildford Surrey UK
Eklund – Nynas Naphthenics Ltd, Wallis House, 76North Street Guildford Surrey UK
One of the most important tools in a condition based maintenance strategy is to have a convenient, reliable and cost efficient method to identify deteriorating condition of a transformer. This method shall preferably be applicable whilst the transformer is on-line. Such a method will reduce the need for invasive maintenance substantially. For transformers, their tap changers, bushing, diverter and oil breakers this tool is the analysis of an oil sample, usually performed in a well equipped off site laboratory. Pump wear, abrasion, overheating, paper and oil ageing, discharge and arcing can all be diagnosed from such a test. An oil sample is taken in periodic intervals, depending on the asset condition and sent toaboratory for analysis. Results from the oil analysis are used to diagnose and assess the condition of the unit.